How roots fans achieve efficiency
The deviation of the pulley can be adjusted with a ruler. After using for a period of time, the belt will become loose, and it should be readjusted at this time.
Check the gear oil. When leaving the factory, the gear oil has been filled in the oil tank, please check the gear oil.
In the stop state, it can be added to the middle of the oil window. Do not add more, otherwise it will cause oil leakage. Remove foreign objects such as welding slag in the pipeline before installation.
The valve should be placed in the fully open state, otherwise the fan will be overloaded and the fan will be damaged.
The foundation design should comply with the relevant regulations of national machinery and equipment installation projects. The foundation should be built on hard soil, and it should be 100-250 mm higher than the ground and 800-1500 mm deep.
The bearing surface of the foundation should be 100-250 mm wider than the base. The foundation should not be connected to other building and wall foundations.
There should be enough space around the high-pressure roots fan to meet the needs of maintenance and disassembly.
In the field of turbine compressors, research on ternary flow impellers has evolved from quasi-ternary flow impellers to full ternary flow impellers.
Moreover, the ternary airflow analysis method has also been developed into the design of the stationary components of the blade diffuser in order to achieve higher unit efficiency.
Ternary flow impellers will also find more and more applications in centrifugal three-leaf roots blowers.
Enlarging the adjustment range and improving the efficiency of high-pressure roots fans under variable load adjustment is also an important part of the efficiency of high-pressure roots fans.
Contact Sanniu Roots Fan
Name: Shandong Sanniu Machinery Co., Ltd.
Customer Service: 0531-83826888
Address: North Industrial Park, Xianggongzhuang Town, Zhangqiu City